Fernox DS-3 LIMESCALE REMOVER
- Restores efficiency to all types of water heater
- Powerful acid limescale remover, dissolves up to 50% of its own weight of limescale
- Corrosion inhibited
- Colour change indicated when exhausted
- Safe to apply and easy to use
Fernox DS-3 is used for removing limescale from any type of water heater to restore its efficiency. It is safe to use with steel, stainless steel, cast iron, copper, brass, PVC, ABS rubber polythene and most plastic pipework.
It should not be used with thin gauge or badly corroded aluminium, zinc, galvanised steel, acrylic (e.g. plastic kettles and baths) chromium plated or enamelled surfaces (e.g. baths), concrete and asbestos. When in doubt check with the appliance manufacturer.
- Fernox DS-3 contains Sulphamic acid with inhibitors, indicators and non-foaming surfactants
- Colour: Yellow
- Odour: Faint
- Form: Crystals
- pH: 2 at 1% w/w in water
- S.G: N/A
Application and Dosage
Fernox DS-3 should first be dissolved in hot water, at the maximum concentration of 1 kg per 10 litres of water and a minimum concentration of 250 g per 10 litres of water (10% - 2.5%). Hot water will accelerate de-scaling but do not exceed 80°C. The de-scaling process will release carbon dioxide gas (CO2), which can cause foaming. Hence, space should be allowed for this before commencing work. A colour change from yellow, through green, to blue indicates the de-scaling power is exhausted. However, the major part of the solution's effort is expended when green is reached and if cold the final change to blue can take a long time. When de-scaling is complete, drain and rinse several times until no traces or odours remain. DS-3 can be neutralised with Fernox Superconcentrate System Neutraliser.
Packaging, Handling and Storage
Fernox DS-3 is supplied in 250 g, 2 kg and 30 kg containers.Fernox DS-3 contains Sulphamic acid and is classified as irritant. Irritating to eyes and skin. Harmful to aquatic organisms, may cause long-term adverse effects in the aquatic environment. Keep out of reach of children. In case of contact with eyes, rinse immediately with plenty of water and seek medical advice. After contact with skin, wash immediately with plenty of water. Avoid release into the environment.
Descaling an entire hot water system
De-scaling a domestic hot water system including the storage cylinder, immersion heater, pipework and taps:
- 1) Turn off boiler and/or the immersion heater
- 2) Tie up the ball valve or isolate mains water supply to the cold water storage tank
- 3) Open all hot water taps and drain the entire system. Close taps
- 4) Fernox DS-3 should first be dissolved in warm water, at the maximum concentration of 1 kg per 10 litres of water, (minimum concentration is 250 g per 10 litres of water)
- 5) i) Connect a funnel to a suitable length of rubber or plastic tubing. The tubing should fit into (or onto) the cylinder feed connection on the inside of the cold water storage tank and the strong acid solution then introduced via the funnel, or:- ii) Where the cold water storage tank serves the hot water cylinder only and no other appliance or outlet, the DS-3 solution can be introduced directly into the tank
- 6) Refill the water system until the water level in the cold water storage tank is just covering the cylinder feed connection. This is to prevent over dilution of the acid solution of minimising the total amount of the water in the system
- 7) Turn on the boiler and/or immersion heater and heat the acid solution in the hot water cylinder to a moderate temperature (50-60oC / 120-140oF) and keep at this temperature for a minimum of 4 hours (max 12 hours)
- 8) Open all hot water taps briefly every 10-15 minutes, allowing ½ - 1 pint of acid solution to run into a plastic container. This is because the acid solution will be neutralised by lime deposits within the pipework and slowly drawing off a small amount of solution will replace spent de-scaler within the pipes. Avoid contact with enamel baths and sinks etc
- 9) Finally, turn off the boiler and immersion heater, and drain the hot water system completely. BALE OUT any residual water from the cold water storage tank as this may contain some DS-3 below the feedpipe connection
- 10) When disposing of spent DS-3 solution it is best neutralised with Fernox Superconcentrate System Neutraliser
- 11) Release the ball valve of the cold water storage tank and thoroughly rinse the entire hot water supply system, opening all hot water taps - Also rinse the cold water system (where applicable) as some acid may have entered via the cold water storage tank.
Here at TradePlumbing.co.uk we have voluntarily extended our returns period to 90 days, as we understand that sometimes there may be the odd item left over from a project or you may have an unexpected delay to a project meaning that you need the added peace of mind when ordering products in case a return is necessary.
We truly believe in being able to offer customers a flexible service and this extended period allows us to go that little extra to help you when in need, as long as goods are returned in the same condition as received we are happy to help.
To return any time initially please email your request to our Customer Support team at email@example.com along with your TP - Order Reference, please allow at least 1 working day for response and we will take it from there.
To View our complete Return Policy Click on Return and Refunds